You cannot put it over anything. You cannot put it next to anything. There must a clear space in front of the panel for an electrician to stand. The space must be kept clear for at least 3 feet in front of the panel, and for 30 inches left to right in front of the panel.
Can a panel be in the kitchen?
Panels in kitchens are good to go, just don’t put a stove, dishwasher, table etc. in front or below it.
Can an electrical panel be in a cabinet?
The NEC only says that the electrical panel is required to be readily accessible, meaning you can get to it without tools, ladders, etc., and that you need clearance in front of the panel 30″ wide and 36″ deep. It does not say that the door is required to open 180 degrees.
Where can I put my electrical panel?
Best Locations for Electrical Panel
- Garages – attached garages are the best location for an electrical panel, as they provide enough space to comply with the clear workspace requirements, but are also quite hidden.
- Basements – the basement is another preferable location for your electrical panel.
How close to a sink can an electrical panel be?
You may install the panelboard as close as you like to a janitorial sink; however, a minimum of 36 in. deep by 30 in. wide of clear working space is required in front of the panelboard [110.26(A)].
Can you put a refrigerator in front of an electrical panel?
Crowding a Service Panel
Here’s a good rule of thumb: If you can’t park a refrigerator in front of the panel, you don’t have enough working space. These clearances are designed to protect the person working on the panel.
How do you cover a kitchen electrical panel?
Strategically placed artwork, framed message boards, or a weaving or tapestry are all viable options for covering up obtrusive electrical eyesores. HGTV suggests inserting child proof safety plugs into unused outlets before covering with artwork.
Where can you not have an electrical panel?
What electrical panel locations are prohibited?
- Where exposed to physical damage.
- In the vicinity of easily ignitable material. Clothes closets are specifically noted as an area with easily ignitable material (hanging clothes).
- In bathrooms.
- Over steps.
What is code for electrical panel?
Breaker panel must be at least 4 feet off the ground, but no higher than 6 feet. The panel door must be able to open at least 90 degrees. Working space around the breaker panel must be at least 30 inches wide and 72 inches from the ground up.
How close can a switch be to a kitchen sink?
Additionally, no point on the wall should be farther than 24 inches from an outlet in either direction (meaning 4 feet total between outlets), so you must have an outlet within 2 feet of the kitchen sink.